BTL Mark: Resolve interoperability issues & increase buyer confidence
Monitoring the Inert: Envelope, Structure
The automation industry, as well as facility designers and managers, may not yet fully appreciate the value and wide-ranging impact of monitoring and management systems designed specifically for the envelope and structure of their buildings.
Jim Sinopoli PE,
RCDD, LEED AP
Smart Buildings LLC
Currently most monitoring of a building’s envelope or structure is done through periodic manual inspections, augmented with handheld devices, tools or instruments. Automating the monitoring process provides several benefits: more timely data, proactively addressing problems or issues, increased comfort and security, lower maintenance costs, data that can guide and support manual inspection, and generally better management of a building’s performance. So if the envelope and structure consists of static materials what could possibly be monitored that would assist in measuring and managing the building’s performance? It turns out there is plenty:
Moisture Intrusion – Obviously if there is moisture in the building envelope there’s a water leak, there could be mold and the integrity of the envelope may be breached. A facility technician can inspect for moisture leaks with a handheld device, but better yet, they can install moisture sensors and a data recorder to continuously monitor the envelope. In new construction sensors can be embedded in the envelope or attached to the structure. Existing buildings are obviously more difficult and sensors would be attached or penetrations may need to be made in order to install sensors. You’ll want to place sensors around locations such as parapet joint flashing, control joints, wall-window interfaces, window jambs, wall-concrete slab interface and all the other places water is likely to gather, settle or get into. There are a number of methods that moisture sensors use to sense moisture. Sensors can measure moisture using the electrical properties of the materials (resistance, capacitance, etc.) which varies with the moisture content of the materials; another method is thermal-based, that is the temperature of the materials caused by moisture.
Wireless is generally the preferred method of
connectivity for moisture intrusion systems and related monitoring of
the envelope or structure where the network can self-configure and
connect back to a data recorder and eventually a workstation or
Building Management Systems (BMS).
Air Leakage - Air leaking through a building envelope not only wastes significant amount of energy but decreases thermal comfort for occupants and allows dust, moisture, noise and airborne pollutants into the building. The detection of air leakage is usually done manually. However, walls can be instrumented to measure air pressure differences which can at least indicate potential issues that may require inspection via a manual air leakage test. Analyzing trending data in a BMS can also help in identifying issues. Trending data would be able to determine changes in space humidity, building pressure, outdoor airflow and temperatures. For example, high relative humidity might indicate negative building pressurization, which may lead to inspection of seals, leaks or equipment.
Structural Loads - Building materials age and degrade over time affecting their structural integrity. Building structures should be monitored for stress, strain, vibration, deflection, displacement and tilt; the data then fully analyzed to determine the current health of the structure. One common building example is steel joist construction used in many commercial buildings to support the roof; the use of strain gauges or sensors can assist a building owner in monitoring the load of the roof when it snows or rains.
Monitoring structural loads in buildings and other assemblies is not new. Probably the best known project involving such monitoring is the rebuilding of the St. Anthony Falls Bridge in Minnesota in 2009 where over 300 sensors were embedded in the bridge to monitor the structure in real-time.
Seismic Monitoring – Although the United States Geological Survey (USGS) detects the location and magnitude of global earthquakes, some building owners deploy their own seismic monitoring system. It uses accelerometers (devices that measure motion and vibration) at specific locations in a building to measure the response of a building’s structure to an earthquake event. Seismic monitoring has several important benefits. For a building owner real-time data as to how the earthquake affected the structure is quicker than and can assist in the physical inspection of the building, thus increasing the chances the building can remain functional or quickly regain functionality. From a government or community response, data from multiple buildings affected by earthquakes can be correlated to assess how the larger area was affected. In many cases, the governmental entity responsible for monitoring earthquakes or geology will have real-time connections and feeds to the building’s seismic data recorder.
in the Structure - Fenestrations
Doors and Operative
Windows - It’s a good practice to monitor each of the major
fenestrations in the envelope simply to identify whether they are open
or closed. That is each exterior door and operative window should have
a switch in its frame to indicate whether the position of the door or
window. Doors that have access control already have such switches but
other doors not covered by access control should have the door position
switch as well. If you have a facility or building management
system that monitors the switches you can create some “exceptions” or
times as to when open doors or windows are acceptable and when they’re
not, and use the information to better manage the building.
External Shading - Exterior shading (adjustable and automated shading that is attached to the building’s envelope) has become one of the popular tools related to energy efficiency. It is not a true fenestration or opening but impacts the performance of the related window. Shading can reduce the demand for cooling and provide a modification of the lighting for a space to improve the amount and dispersal of the light. Most exterior shading systems (as well as some lighting control systems) are driven by the sun position, solar intensity, sky position, BTU Load, readings from indoor and outdoor photo sensors and radiometers (devices that measure radiation). The shading system will position itself based on the control software application to determine the best position for the shade as indicated from the sensor data. The shading system, because it will control the thermal load and amount of light entering the space, will drive lighting levels and impact the HVAC system.
Electrically Switchable Glass - Electrically switchable glass is basically glass, glazing or coatings that change light transmission properties when voltage is applied. There are a variety of technical means to accomplish this including electrochromic, suspended particles and liquid crystals devices with different approaches and capabilities among the technical means. When voltage is applied to electrically switchable glass it changes to tint and absorbs light. The tint level can be controlled manually or automated via integration into a BAS system. Much like motorized shades electrically switchable glass can be manually operated via a switch or automated based on light sensors, schedule, occupancy sensors, lighting control or thermostats.
Building Integrated PV - There is now a substantial and growing movement to integrate photovoltaics (PV) into building components. The major components are the facade, which is essentially the exterior of the building including curtain walls, spandrel panels, etc., and roofing systems, including tiles, shingles, standing seam products for steel roofs and skylights. The solar energy requires managing and monitoring of the solar cells.
The automation industry, as well as facility designers and managers,
may not yet fully appreciate the value and wide-ranging impact of
monitoring and management systems designed specifically for the
envelope and structure of their buildings. The big idea is quite simply
that basic data for the entire building must be transformed into
relevant information which in turn provides the foundation for better
For more information about smart buildings, technology design or to schedule a Continuing Education program, email firstname.lastname@example.org.
[Click Banner To Learn More]
[Home Page] [The Automator] [About] [Subscribe ] [Contact Us]