Innovations in Comfort, Efficiency, and Safety Solutions.
– No Longer Optional
& Angela Lewis
March Issue - BAS Column
At one time, it might have been acceptable to view controls as a
“necessary evil” with little attention given to the details of design
including sequences and commissioning. To deliver high
performance buildings today requires systems optimization with special
detailed attention to controls design and delivery. As state
energy codes move to the latest versions of ASHRAE 90.1, even
conventional new buildings will need to be high performance. This
moves controls design to being a necessity to help meet required
This month we are going to look at some of the key optimization strategies that you should consider for both current and upcoming projects.
There are a few fundamental concepts we always come back to in order to optimize any system. These include:
From the above four fundamental strategies, you can then develop a
series of optimization strategies. Note that not all of these
strategies apply to every project, and these do not include all of the
necessary strategies and sequences required for proper and safe
Air Side: These are strategies that are applied to airside systems including both applied and unitary air handling equipment and their associated terminal units.
Static Pressure Reset: The supply fan speed is varied so that it only provides enough air to satisfy the most demanding VAV terminal. This is achieved by controlling the fan to meet a static pressure setpoint, which is dynamically reset based on the most extreme box position. This strategy matches both airflow and static pressure to meet the demands of the system.
Supply Air Reset: Raise the supply air setpoint when the majority of boxes are in their heating mode. This strategy balances out the need for reheating while still holding down fan energy usage.
Demand Controlled Ventilation: Adjust the People Outdoor Air Rate (Rp) based on building occupancy. This is generally done with the use of CO2 sensing but other mechanisms for occupant counting can also be used.
Single Zone VAV: Utilize a VFD on a single zone air handler and modulate the fan speed, along with discharge air temperature, to meet the zones demands.
Occupancy Based Control: Schedule based on occupancy, down to the zone level. This can be done by scheduling groups of VAV terminals, or with the use of occupancy sensors. Look for opportunities to coordinate occupancy to also schedule lighting.
Economizer Optimization: Whenever possible, utilize outdoor air for cooling. Strategies for economizer changeover can provide more hours of economizer operation reducing the load for mechanical cooling.
Central Energy Plant: The central energy plant may include chillers, boilers, pumps and towers.
Chiller and Boiler Sequencing: Select the most efficient machine(s) to meet the plant load. This requires information about the plant load, machine efficiency and availability.
Condenser Water Reset: For water cooled systems, balance energy use between the towers and chillers to minimize overall energy usage by placing as much work as possible onto the cooling towers.
Variable Primary Flow: Only move as much water as needed to meet the building-cooling load. The use of variable primary flow is the most efficient option. Proper control requires control of system static. Measurement and control of plant flow is also highly recommended.
Following the basics and developing the required optimization sequences are invaluable for high performance building operations. To make these viable though requires careful design including detailed sequences and points lists. Finally, controls commissioning to verify proper operations is essential!
About the Authors
Paul and Ira first worked together on a series of ASHRAE projects including the BACnet committee and Guideline 13 – Specifying DDC Controls. The formation of Building Intelligence Group provided them the ability to work together professionally providing assistance to owners with the planning, design and development of Intelligent Building Systems. Building Intelligence Group provides services for clients worldwide including leading Universities, Corporations, and Developers. More information can be found at www.buildingintelligencegroup.com We also invite you to contact us directly at Paul@buildingintelligencegroup.com or email@example.com
[Click Banner To Learn More]
[Home Page] [The Automator] [About] [Subscribe ] [Contact Us]